This task, to my knowledge is only available on the Hayward Goldline/Aqua Rite units.
|If your salt cell reading is not responding as it should, or seems unrealistically low,
you may need to recalibrate the cell, or the unit will stop working when it hits the low salt
- Make sure that the Turbo Cell is clean and has no buildup of calcium or debris to cause
erroneous salt readings.
- With the filter pump running, switch the Controller power switch down to the "Off"
position, and then back up to "Auto". You should hear a click within 10 or 15
seconds. When you do, press the diagnostic button five times in a row. The system
will go through a recalibration process.
- Wait until the numbers stop changing. If the system settles on or near a number that
is close to what you believe to be the salt level in the pool, slide the power switch up to
"Super Chlorinate", then back down to "Auto". This will lock that number in as the new average
Replacement parts/systems :